It would be appropriate to say that industrial control panels are the back bone of many activities in the world today such as water treatment, lift stations, main control cabinets, and OEM supplied equipment. The design of an industrial control panel depends on a variety of different articles in the NEC (National Electrical Code). This meant that there was widespread confusion in this regard. This would eventually lead to introduction of the NEC 409. Industrial control panels are defined as an assembly of standard and systematic arrangements of more than one control components according to the NEC 409.
These control components can include:
The workings of an industrial control panel are closely related to its design. These panels are designed in a way that they are able to tackle an enclosure complemented custom application. Once the enclosure that is closed is opened, there is a vast area available to add valves, multiple motors, etc. The power and the signals that are equally important are routed via specially designed, specialized wires. Yet, there remain some areas of concern in industrial control panels that need to be eradicated as soon as possible.
The only way to eradicate these limitations is to have a major shift in the design of the industrial control panels to make it stay more in line with NEC 409 110(3) requirements.
The SCCR simply put is the amount of energy that a device needs to take into without having to affect the control panel. The role of the SCCR has been to make sure that the workers in and around the control panels are protected. Before the NC 409 was introduced, the designers of industrial control panels could have been forgiven for being unaware of the topic. This would mean that control panels made back then were prone to errors and vulnerabilities. The introduction of the NEC 409 and the SCCR has meant that the control panels have now become more reliable by allowing a greater current withstanding ability in the device.
NEC 110 .9 warrants the installed equipment to be able to withstand a certain amount of fault current without affecting the industrial panel. Yet the NEC 409 110 only requires the builders of the panels to mark the panels. The 409 requirements lack in this regard since they do not specifically state the need for builders to make sure that their devices are able to withstand a certain amount of fault current. The best way to tackle such a situation is to make sure that in addition to the NEC 409, the engineers and the makers of the industrial panel adhere to the requirements of the NEC 110.9 as well.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
Situation A popular chemical compound that often requires heating is wax, which is an organic compou...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainl...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
Wattco Immersion Heaters: A Guide
Immersion Heaters Immersion heaters are some of Wattco’s most popular products. They are one of th...
Applications of Tubular Heating Elements
Tubular heating elements are commonly used in industrial heating due to their versatility and afford...
What is a Screw Plug Heater?
A screw plug heater is a subcategory of immersion heaters, which typically requires small space to o...
A Closer look at Circulation Heaters
Wattco manufactures and designs circulation heaters for maximum efficiency. As a result, these heate...
Electric heating elements have a wide range of uses and applications in many processing and industri...
. Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproce...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
Wattco’s Guide to Industrial Heaters for the Chemical Industry
In the 21st century we have our ability to control heat to thank for much of the technology which im...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
Preheaters of Natural Gas
Natural gas is one of the most commonly used fossil fuel and a nonrenewable source of energy....