A control system is an essential part of every industrial heating system. Whereas some applications may require a control system more than others, it is important to ensure that all process heating systems have a proper control panel. A process control enhances the performance of a thermal system and helps to extend the life of an electric heater. There are different types of controls for industrial thermal systems. These controls vary in accuracy and performance.
The PID controls and the bulb-and-capillary thermostats are the most common types of temperature controls used in industrial electric heating systems.
A PID is a three-mode controller that integrates proportional, integral, and derivative actions to provide stable and accurate temperature control. Its integral and derivative actions make it a suitable choice for complex thermal systems. This temperature controller can accept an input from a variety of sensors including resistance temperature detectors (RTDs) and thermocouples. It outputs a voltage that can be used to control a variety of devices. These include electromechanical contractors and mercury displacement relays (MDRs). Refer to some of these temperature control panels.
A bulb-and capillary thermostat is an easy to operate temperature control system that is suitable for applications that don’t require high-accuracy control. As temperature rises, it causes the fluid to expand. The expanding fluid turns the switch off as the temperature approaches the desired temperature set by the operator. As the fluid in the capillary cools, the switch turns on and provides a control voltage to a mercury displacement relay (MDR) or an electromechanical relay.
The following are the most common power switching devices used in process heating systems:
Electromechanical relays have low accuracy, limited life, and generate a significant amount of electrical noise. For best performance, the minimum cycle time should be 30 seconds. The temperature control provides a control voltage that causes the contacts to come together. This completes the circuit and supplies the heater with voltage. An electromechanical relay subjects a heater to thermal shock resulting in shortened life.
An MDR operates like an electromechanical relay except that it uses mercury as the contact element. This control panel offers a cycle time of 5 seconds and it is therefore faster than an electromechanical relay. An MDR generates heat and electrical noise but offers a longer relay and heater life as compared to an electromechanical relay. Environmental regulations discourage use of MDRs in industrial processes.
Solid-state relays have good accuracy but they generate considerable amounts of heat. For best performance, these control devices should be used in vented electrical enclosures. With a cycle time of 1 second, solid-state relays find many applications in process heating systems that demand high accuracy. In addition, a solid-state relay generates minimum noise and it helps to lengthen the life of an electric heater.
An SCR power control panel offers many advantages including extended heater life, reduced maintenance costs, and precise control of the thermal process. An SCR power control can cycle as fast as 8ms. When used properly, this control device can cycle on and off for up to 1,000,000,000 times. This means that an SCR power controller can provide reliable service for many years. This control panel generates heat and higher current units should have a cooling mechanism. Just like solid-state relays, SCR power controls produce little electrical noise.
Wattco offers top of the line digital, temperature control panels designed to fit your needs. For more information. refer to some of our case studies on digital control panels, or contact our experts today to discover more ways our electric heating products can benefit your business.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
The Benefits of Using Over the Side Heaters
For many businesses, it is essential to have access to a method for maintaining water and/or viscous...
COME VISIT US AS THE 2018 LUMEN – PLAN DU SALON MONTRÉAL – STAND #1015
THE LARGEST ELECTRICAL INDUSTRY EXHIBITION IN QUEBEC! @ the Palais des congrès de Montréal. See...
Wattco Immersion Heaters in The Food Industry
The food manufacturing industry requires dependable, efficient industrial heating equipment to creat...
Retrofitting Equipment With Electric Immersion Heaters: A Guide
Electric power is in high demand for industrial heating. It’s more efficient and cost-effective th...
Immersion Heaters for Process Fluids
Process fluids are found in every major industry, and process fluid heating is an essential t...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
Preheaters of Natural Gas
Natural gas is one of the most commonly used fossil fuel and a nonrenewable source of energy. It ...