Proper maintenance of your immersion heater will drastically improve performance, efficiency, and increase lifespan. Being proactive about heater care saves money, and increases safety. This guide covers proper immersion heater maintenance for maximizing lifespan and efficiency.
We will discuss pre-installation, installation, and ongoing care.
Long term care starts with picking the right immersion heater. Ensuring that it is constructed of the right material for a specific applications and medium is one of the most important aspects in immersion heater lifespan and efficiency. The materials used for your immersion heater needs to be able to stand up to its use conditions. Incoloy or stainless steel, for example, may be used when heating corrosive mediums because they are more resistant to corrosion.
The Megohm Reading is used to gather a resistance reading before the heater is connected to a power source. This reading will help to identify if the heater has been exposed to moisture in transportation or storage. Moisture may cause problems post-installation or cause damage to the heater over time.
Moisture can be removed by baking the heater in an oven or by energizing the heaters at a low voltage.
Before installing the immersion heater, the seals and connections should be checked. This check is to ensure the connections are tight and that there are no leaks. The gasket between the heater and the tank should be drip proof.
Tight connections and functional seals will prevent energy loss and damage to the heater.
Proper wiring will help prevent damage to the immersion heater as well as ensuring it is operating safely and efficiently.
Check to ensure you have the right wire temperature rating. The rating often requires 200゜ degrees C or higher. The wires must be capable of meeting the rating requirements to effectively supply the heater.
In this same vein, it is important to make sure the mains supply corresponds with the voltage on the heater and the correct supply cable sizes for the electrical load being used.
Ensure temperature control mechanisms are in place to prevent overheating – this will protect both the liquid and the heater.
The wiring for the thermostat and safety cutout is especially important. First and foremost, this is a safety concern. The heater must be able to cut out if the thermostat detects that the temperature is out of the optimal range.
When mounting your immersion heater, location is very important for longevity, efficiency, and for access to perform ongoing maintenance. The heater should be placed where it has enough clearance to be easily removed. This will make it easy for ongoing maintenance in the future when the heater needs to be removed for cleaning.
The location of the heater should be where it is safest from shock, vibration, dust, corrosion, or explosion. If the unit has been specifically made to withstand these elements, then it has more options for location. However, the heater should not be placed where sludge, sediments, or deposits will settle on it. When sediment settles on the immersion heater in can act as an insulator, reducing efficiency and reducing the heater’s lifespan.
Ensure the active part of the element is submerged. Put switches in place to shut off the heater if the fluid level drops too low. If the fluid drops too low without the immersion heater shutting off it can result in damage to the heater which will reduce its lifespan and operating efficiency.
Routine checkups should be performed, even when your immersion heater is functioning properly. It is more effective and inexpensive to be proactive with the care of your heater than to wait for symptoms to occur.
Before removing your immersion heater you must ensure it is turned off. If the heater is left on it can create a safety hazard for those performing the maintenance. As well, removing the heater while it is still on risks causing damage to the heater.
Perform regular checks of the coatings to check for corrosion. If corrosion is found the terminal enclosure gasket should be checked. If any sign of corrosion is found here, the gasket should be replaced. A leak here could cause significant damage to the entire system.
Check connections for tightness. If there is a loose connection resistance heat can be created inside the system. This resistance heat can cause the heater terminal to melt.
Although you installed the immersion heater where it was less likely for sediment to gather, periodic checks should still be performed. If there is sediment, it should be removed to prevent damage. If sediment is building up quickly or frequently, consider finding a new location for the heater. Cleaning can generally be performed with something as simple as a damp cloth. For tougher sediment, a power washer can be used on a low power setting.
The fluid level should be regularly checked to ensure the heating elements are submerged. Testing the fluid level sensors and safety shutoff is a proactive way to prevent damage to the equipment and medium.
Picking the right immersion heater for maximum efficiency and lifespan is an important process and can be a difficult choice to make. Contact our expert staff today for recommendations and support.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
Situation A popular chemical compound that often requires heating is wax, which is an organic compou...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainl...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
Radiant Heating with Infrared Heaters: Types and Applications
An Introduction to Infrared Heaters Infrared heaters are commonly used in large indoor and outdoor a...
Heating and Storing Asphalt Part 2
This article is a continuation of the previous article titled the “Heating and Storing Asphalt Par...
How to Prevent Liquids from Freezing Using Immersion Heaters?
Industries whose productions are aqueous or liquid-based like the oil and gas sector, strive to prot...
Why Over-The-Side Immersion Heaters are Used in Petrochemical Industry?
Over-the side immersion heaters have great significance in the petrochemical industry as they are re...
Certain substances will react with the atmosphere due to their chemical composition. A slice of appl...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
Wattco’s Guide to Industrial Heaters for the Chemical Industry
In the 21st century we have our ability to control heat to thank for much of the technology which im...
Preheaters of Natural Gas
Natural gas is one of the most commonly used fossil fuel and a nonrenewable source of energy. It ...