Freeze Protection: With many weather conditions being unpredictable year after year, many companies look at protecting their mediums. Approaches change depending on whether they are water-based, or oil-based from freezing through the winter months. In a study conducted by the University of California for Atmospheric Science in 2000*, it was regarded that more economic losses occur due to freeze damage in the United States. More than any other weather-related hazard.
The most common industries generally affected over the winter months are the Oil and Gas industry, Water treatment plants, Transportation industry, Agriculture, and Mining industry. These industries have many applications that require storing their product outside. Thus exposing it to extreme temperature for a long period of time.
With water-based products, freeze protection is vital as they begin to crystallize and freeze at 0°C / 32°F / 273.15K. Keep in mind, that providing a heat source alone is not always the best solution. It’s important to make sure that tanks or reservoirs are properly insulated to assure that the medium doesn’t freeze.
When dealing with oil-based products however, it becomes more difficult the colder the weather temperature changes. Fuel oils (both clear Diesel fuel and dyed home heating oil) do not freeze, but rather turn into gel or a thicker wax. This process begins to occur below 32°F, and continuously hardens the colder it gets.
Once the temperature drops below 15°F the wax in the fuel begins to crystallize and separate from the oil. This makes it extremely difficult to handle or to remove from its container. In certain applications where these fuel oils are transported through a pipeline, it is highly recommended to insulate any piping that may be exposed to extreme temperature and winds, in order to avoid any clogged pipes.
For Motor oil, Gear oil and Hydraulic Oil each has a different freezing temperature range. For instance, Motor working oil (10W30) freezes at –20°F, but from 50°F, to 0F the viscosity of the oil becomes more and more difficult to handle. With Gear oil and Hydraulic oil it’s freezing temperature is set for –10°F. And, same as motor oil, it becomes less viscous the colder it gets. However there are certain oils that do work below freezing temperature and those are generally the thicker kind of Motor Oil’s like 15W30, which freezes at -55°F.
Freeze protection means that you don’t want your tank’s temperature to go below 32°F, or else the liquid will freeze. To best protection against freezing is to insulate your tank. This allows having a heat loss of approx.5%, versus a 35-45% heat loss without any insulation. Since your tank holds a certain amount of gallons, and you’ve decided to only use one heater, insulating your tank is a must. This will avoid having 2 different temperature zones, in your tank. Keep in mind that if your heater is on one side, heat transfer will take some time before getting to the other side, but with insulation, it will get there faster. The most efficient way, however, is to install 2 or more heaters depending on the size of your tank.
The most difficult part of protecting your medium from freezing is determining how much power is enough. The first thing you require is to understand your tanks environment and it’s surroundings. Consult historical charts to determine how cold your location gets with and without the wind. However, the weather is always unpredictable, and you have to keep in mind that if your tank is well insulated, and the heater is working with the proper controls then during the freeze period you should be well protected to bare the storm. In certain regions around the world the temperature will reach below 32°F, and stay below 32°F for a considerable amount of time, this is where the right amount of power and insulation for your tank play their most important role in protecting you against freezing conditions.
These are the formulas that are generally used in the heating industry to determine how many Kilowatts would be required to heat a tank filled with either Water or Oil:
§ [Formula for heating water in a tank]
(# Of Gallons) x (Delta Temperature in Fahrenheit) / (372) x (# hours) = Kilowatts required
§ [Formula for heating oil in a tank]
(# Of Gallons) x (Delta Temperature in Fahrenheit) / (860) x (# hours) = Kilowatts required
How much power is required to protect your Water or Oil tank? For this exercise, we use the formula above, and take into consideration that we are heating 30,000 gallons of water. The next step is to determine the delta temperature, the ambient temperature of the water tank will start at approx. 40°F and your target temperature will be 80°F, that’s a Delta Temperature Rise of 40°F.
We would then use the formula, (30,000 gallons) x (40°F DT) / (372) x (24 hours) = 134KW/per hour. This means that for every hour that passes your 30,000 gallons of water will increment by approx. 1.66°F/ per hour, for the next 24 hours. If your tank doesn’t have any insulation, and the exterior temperature of the tank were to drop below 32°F, you would be losing up to 40% of the heat from the side wall of your tank every hour, depending on the thickness of your tank walls.
With your tank being set at a target temperature of 80°F, it would then drop approx. 32°F every hour. Your heater would only increase the temperature by 1.66°F. Which means that half the tank would be frozen in approx. 2 to 3 hours. The other half of the tank where the heater is located would be preparing to crystallize, while a cavity of ice will begin to form around the heater.
This is the primary reason we recommend insulating any tank that’s exposed to the outside weather conditions. It’s the first line of defence for freeze protection because it will shield your tank from the extreme winds and temperatures of winter. With insulation, you only lose approx. 5 % if the temperature drops below 32°F, which if we were to take the same example as above, at 80F you would lose approx. 4F from your outer walls every hour, but with a 134KW heater your increase would be approx. 1.66°F for a difference of a loss in temperature of 2.34°F every hour.
In this example, the current heater won’t provide enough heat and would take approx. 21 to 30 hours before arriving at the freezing point, considering that weather conditions are at below 32°F for more than 24 hours. In certain regions they would experience these types of extreme temperatures for weeks and for other locations would only experience it for a few hours.
The correct amount of power will be always determined by location. For example, consider a tank in Denver, Colorado. The average temperature for the winter months is below 32°F. So you would need a heater that matches or exceeds your heat loss. Using the same example as above, you require a 350KW heater to heat 30,000 gallons of water to a rise in temperature of 4.34°F/ every hour.
However, if your tank was located in Tennessee where they experience freezing condition for only a few hours, then using a 170KW heater would be enough because your temperature rise every hour would be 2.2°F and would be efficient enough to maintain a working temperature for up to 72 hours, before it drops below the freezing point.
Another important addition to freeze protection is controls for your heater to manage efficiently both temperature and power output. In certain cases, the amperage required to run these type of heaters is very high. That’s why we recommend including a step controller and a hi-limit protection system to protect your investment from failure.
As a rule of thumb, when dealing with extreme winter weather it is always better to have more power behind your heater, then to come up short and turn your tank into the worlds largest Popsicle. Remember that your first line of defence is to always insulate your tank, probably the smallest investment with most benefits. For any further details regarding freeze protection, or if you have any questions pertaining to a project you’re currently working on and need some help, please don’t hesitate to contact me. Best Regards and keep warm.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
Importance of Coal in the Energy Sector Coal is always considered as a vital fundamental source of t...
COME VISIT US AS THE 2016 ADIPEC SHOW IN ABU DHABI
The world’s most important oil and gas exhibition show will feature Wattco’s latest tech...
Applications of Over-The-Side heaters in the Chemical Industry
Top 7 Most Useful Features of Circulation Immersion Heaters
Circulation immersion heaters are a special type of industrial heater that contain packaged units de...
Process Heating with Immersion Heaters
Process heating is an important part of industry today, especially in the defense, chemical, and oil...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
What is a Pressure Vessel?
Pressure vessels are carefully fabricated, enclosed containers designed for the purpose of holding e...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...