Load banks are essential for applications in a variety of industrial applications, especially for testing power sources. A load bank provides a contained and fully controllable load for predictable and measurable use. They mimic average and peak loads allowing for testing and measurement of how a power source will perform in operation.
In testing, the load bank creates an electrical load and applies it to the power source. The objective of this is to mimic the operational load of the power source in use. Load banks may also support or protect the power source while in operation.
There are a variety of load banks with specific purposes. It is important to match your load bank to your application for the most accurate results. The most common types of load banks include:
The most common type of load bank is resistive. A resistive load bank loads the power source and the engine or motor equally. It removes energy from the complete generating system. It generated the load by converting the systems electrical energy to heat using power resistors. The heat is then dissipated by means of convection. Although building resistive load banks in place is possible, they are generally moveable. This mobility makes it possible to use them on multiple generators in sequence. A stationary resistive load bank gets less use and is more expensive to replace.
An inductive load bank provides a reactive load. It creates a lagging power factor load. The inductive load is often used with a resistive load to simulate mixed loads that a power source may deal with in real operation. The most common ratio has the inductive load at ¾ the load of the resistive load. Where resistive loads simulate loads in ideal conditions, reactive loads simulate real-world operating conditions.
A capacitive load bank also provides a reactive load. However, it creates a leading power factor load, unlike the lagging power factor load of inductive load banks. They are most common in applications with non-linear loads, such as industries using an uninterruptible power supply.
Electronic load banks are becoming more popular. Although reactive load banks are cheaper to purchase, electronic load banks are more precise and sophisticated instruments. They are fully programmable and can leverage automation for efficient and/or continual use. The precision and reliability of electronic load banks make them the primary choice for hospitals and aeronautics, as well as transport, telecom, and mining industries.
Load banks play an important role in most major industries. They are especially important in applications using generators, batteries, and other power sources.
Today, there is a growing demand to reduce our dependence on nonrenewable energy sources. Wind power is touted as one of the key solutions. The most common way to harness this power is through wind turbines. The problem with wind turbines is that their operation can be inefficient, or even have a negative environmental impact through energy wastage. Before building a windmill, testing is a necessity to ensure its efficiency. This is where load banks come in. Load banks are used to verify the functionality of wind turbines. They simulate operation to determine malfunctions and other issues.
WATTCO manufactures electronic load banks that offer the highest degree of precision and control. They offer the same commitment to quality and reliability as all our products. Each WATTCO load bank is customized to customer specifications. Materials, sizes, and shapes are made to fit function and application. Electronic load banks are not only sophisticated, accurate tools, they also have all the benefits of electric power:
WATTCO manufactures load banks that are customizable to your specific needs. If you are purchasing a load bank contact a WATTCO representative today to request a quote. They will help you decide on the right build for your application.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
Why Are Flanged Heaters So Efficient?
Do you have a specific need to heat pressurized fluids? If so, you may wish to take a look at the ma...
How to Reduce Heating Costs for Circulation Heaters
Heating is an essential task in most industrial applications. Operating on a large scale, any energy...
Methods of Industrial Oil Flushing
Industry machinery and equipment can be touchy sometimes. Hydraulic and lubrication systems need car...
A Comprehensive Look at the Water Heater Element
A water heater element is a specific tool or a part within the cylindrical unit of the heater that p...
Tank Heating and Flanged Heaters
Whether your company is in the food industry, the oil industry or has another industrial application...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
What is a Pressure Vessel?
Pressure vessels are carefully fabricated, enclosed containers designed for the purpose of holding e...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...