When an electric motor starts at full voltage, the inrush current can be up to 8 times higher than the nameplate value. Without a motor starter, the high inrush current and starting torque can cause damage over time. Many motor starting systems prevent this, including soft starters and variable frequency drives (VFD). While both devices use a similar starting method, there are also important differences.
Selecting the right starting system is important when specifying motor controls. Soft starters reduce the inrush current and torque for motors that don’t require speed control when operating. On the other hand, a VFD lowers the inrush current, but it can also reduce rpm while the motor operates. Since VFDs provide speed control, they have a higher price than soft starters for a given motor capacity.
A soft starter uses electronic components called thyristors to control the starting voltage applied to a motor. Instead of applying the rated voltage at once, thyristors increase the voltage gradually as the motor accelerates. By reducing the inrush current and torque, soft starters can increase the service life of electric motors.
A soft starter for a three-phase motor uses six thyristors, which are arranged in back-to-back pairs called triac circuits:
A soft starter only reduces voltage, while frequency stays at 60Hz or 50Hz depending on the country. Since the speed of an operating motor depends on frequency, a soft starter cannot be used for speed control. Reduced voltage can limit the starting current of a motor, but it will not reduce rpm once the unit has started. Actually, a motor overheats with reduced voltage, and this affects its service life.
Soft starters can be used with any compatible motors. They are especially useful for starting high-inertia loads, where the inrush current and torque would be very high at full voltage. Industrial conveyors and dust collectors are two examples of these loads.
A VFD can be used for both motor starting and speed control. This requires a more complex circuit, which has three main parts:
Using these circuits, a VFD can reduce both the voltage and the frequency applied to an electric motor. Like a soft starter, a VFD applies a lower starting voltage to reduce current and torque. A VFD improves control over the starting torque since it can also control frequency.
Once a motor is running, a VFD can slow it down by reducing voltage and frequency. Reducing voltage and frequency together prevents overheating. As such, the VFD does not damage the motor.
VFDs are useful in applications where the motor workload varies, such as HVAC and pumping systems. Electric motors consume less power when running at reduced speed, and energy consultants often recommend VFDs for this reason.
When comparing a soft starter and a VFD, the best option depends on the application. VFDs have higher prices than soft starters for a given capacity since they can also control motor speed. However, the extra cost of a VFD is compensated by the energy savings from running at reduced speed.
We do not recommend VFDs for starting motors that always run at full speed. These motors offer no chances to save energy with speed reduction. Soft starters are the best option in these cases since they accomplish the same function while being less expensive. Having fewer components, soft starters are also more compact than VFDs.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
A Look at Industrial Immersion Heaters for Tanks in Cold Weather
Industries such as petrochemical industry, process-heating industry and chemical industry have indus...
Crash Course on Duct Heaters
What are Duct Heaters? It’s easy to understand what duct heaters are just by considering their n...
Electric Boiler Heaters For Clean Steam & Pure Steam
Steam is one of the best heat carriers in process industries. It’s used for everything from space ...
Different Components of a Wattco Digital Controller
The introduction of digital controllers in Wattco heating devices has brought about revolutionary ch...
Heating and Storing Asphalt Part 2
This article is a continuation of the previous article titled the “Heating and Storing Asphalt Par...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
What is a Pressure Vessel?
Pressure vessels are carefully fabricated, enclosed containers designed for the purpose of holding e...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...