Electric motors have many applications in residential, commercial, and industrial settings. To accomplish their intended functions, they require reliable control and protection. Motors face exposure to several hazards that can reduce their service life. As well as major electrical faults can damage them beyond repair.
Well-designed motor control is complemented with adequate protection devices. The following are some of the main electrical hazards that must be considered:
Given the range of hazards to which they are exposed, electric motors must use a combination of devices. This article provides an overview of the most common protective features.
A motor circuit protector is a magnetic device that responds to the current drawn by a motor. This device offers protection against high-current hazards. For example, short circuits, ground faults, and stalling during start-up. The magnetic field caused by these currents triggers the MCP, which disconnects the power supply to protect the motor.
An MCP does not respond to minor overloads, voltage issues, and phase imbalance, since these events do not produce a current peak. Therefore, other protection devices are necessary for these electrical hazards.
Overload occurs when an electric motor draws continuous current above its nameplate value. This causes overheating. Even if a motor is slightly above rated current, it is still considered an overload.
An overload relay is a protection device with a slight delay in its response. This allows high-current events with a short duration, such as the inrush current when starting. An overload relay disconnects a motor when a current peak lasts longer than expected in normal operation. Based on their operating principle, overload relays can be described as thermal or electronic:
Electronic overload relays are more accurate and unaffected by ambient temperature. This is because they do not rely on thermal expansion. Although, they are also more expensive than thermal relays.
A motor protection circuit breaker is a combined device. It has both an instant response and a delayed response. An MPCB has a magnetic protection element similar to an MCP. The element disconnects the motor immediately in response to high currents. Such as those caused by short circuits and ground faults. However, an MPCB also includes a delayed response like an overload relay. Which can be thermal or electronic.
In a few words, an MPCB combines the functions of an MCP and an overload relay. Additional protections are still necessary for voltage and phase issues.
Ideally, a three-phase motor should operate at rated voltage, and the phase voltages should be perfectly balanced. Yet, achieving this is unlikely in actual projects, and there is some tolerance for voltage variation and phase imbalance:
Electric motors can also be affected by single-phasing. Which occurs when one phase is disconnected completely. A motor can continue running in this condition. But it becomes unstable and its windings overheat. Also, noise and vibration increase with single-phasing.
Motors can also be affected by phase reversal. Which happens when two-phase voltages are switched. A phase reversal causes the motor to rotate in reverse, and the consequences will depend on the load. For example, a fan will move air in the opposite direction. But heavy industrial motors with the wrong phase sequence can cause severe accidents.
A voltage monitoring relay disconnects a motor when its operating voltage falls outside the optimal range. Typically, within 10% of the rated voltage. On the other hand, a phase monitoring relay disconnects a motor in response to phase loss, reversal, and excessive imbalance.
Electric motors need adequate controls and protection devices to meet their performance and safety requirements. Many electrical hazards can affect motors. No single protection device cannot respond to all. For this reason, motor controls must combine various protective features.
The specific protection requirements for electric motors depends on the application. But in general, they must be guarded against voltage variations and excessive current. In the case of three-phase motors, protection devices must also ensure that phases are balanced and sequenced correctly.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
Hot Oil Heating vs Steam Boiler Systems for Tank Heating
There is a big increase in demand for electric circulation heaters. Yet, for tank heaters, steam boi...
Save Money: The Many Uses of Industrial Immersion Heaters
Industrial level immersion heaters are a great option for industry leaders because they represent ...
Advantages of Electric Immersion Heaters in Chemical Manufacturing
The chemical manufacturing industry has unique challenges in the production, storage, and transporta...
Signs That It’s Time To Replace Your Immersion Heater
A Quick Refresher on When to Replace an Industrial Heater Electric immersion heaters are designed fo...
Unique Considerations When Choosing An Immersion Heater
It is important to choose the right immersion heater for your specific application to get the most ...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
What is a Pressure Vessel?
Pressure vessels are carefully fabricated, enclosed containers designed for the purpose of holding e...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...