Hot oil heating systems operate within a closed loop, with the heat transfer fluid recirculating through the heater elements. This method of heating makes circulation heaters extremely efficient and capable of accurate temperature maintenance.
Electric circulation heaters use a simple design that results in longer lifespans and easy maintenance. As such, if there is a decrease in performance, thermal fluid degradation is a likely culprit. As thermal fluid degrades, it can alter the flow, overwork the heating system, and cause damage.
In this article, we look at how to identify causes of heat degradation and how to prevent them before they become an issue.
The most common cause of thermal fluid degradation is overheating. When the fluid is maintained at too high of a temperature a breaking, or cracking, of fluid molecules begins. As a result, the viscosity of the fluid decreases, and calcification can occur.
Without active maintenance, the resulting calcification can deteriorate the piping and heating equipment. As well, the decreased viscosity will affect the efficiency, quality, and reliability of your heating process.
When fluid and air come into contact at elevated temperatures oxidation occurs. When oxygen is introduced into a circulation heater, it is the perfect environment for this reaction to occur. The oxidation process results in poor thermal stability in the heat transfer fluid.
The poor thermal stability affects the viscosity of the fluid, creating sludge and buildups within the heating system. This decreases the flow rate, overtaxes the heater, and prevents efficient, reliable heating.
One of the key ways to avoid thermal fluid damage is by using systems that provide precision heating. Improving the accuracy of measuring, monitoring, and maintaining heat throughout the system serves to prevent overheating.
This accuracy is a major benefit of using electric circulation heaters. Using electricity allows for much greater precision and greater responsiveness. Customization of industrial heaters is also important to make sure the wattages, materials, and configurations are appropriate for each project.
Thermal fluid heater maintenance is one of the most important ways to preserve the integrity and efficiency of your heater and its heat transfer fluid. Proper maintenance not only helps to resolve and prevent degradation but also decreases the need for expensive repairs and increases heater longevity.
Routine maintenance may include inspections, cleaning, and hot oil flushing. These techniques serve to remove contaminants, prevent sludge and calcium buildups, and keep everything in good working order.
During installation and maintenance, careful selection and inspection of all valves and connections are important. Check to ensure they fit properly, are not loosening, and provide no gaps for liquid or air. Reliable connections protect fluid integrity by reducing the risk of oxidation. As well, they help control movement to the expansion tank and reduce fluid loss.
Insulation also plays a valuable role in protecting thermal fluids. It is the most economical way to passively prevent heat loss. This helps keep temperatures in the system stable, while simultaneously decreasing the amount of energy the heater uses. As a result, the fluid integrity is protected and operational costs are lower.
Wattco custom-manufactures electric circulation and thermal fluid heaters. Our team of engineers works with you and your budget to choose the ideal wattages, configurations, heater types, and materials for your specific project. This careful selection helps to ensure the integrity of your thermal fluid, increase the efficiency of your heater, and make your process more reliable.
Contact Wattco today for circulation heater quotes and information.
Why is Mineral Oil Used in Thermal Heaters?
Thermal heaters, also known as thermal fluid heaters, employ the use of a thermal liquid such as wat...
What to Use When Heating Wax
SituationA popular chemical compound that often requires heating is wax, which is an organic compoun...
What is Passivation? Why do We Need to Passivate Flanged Heaters?
Most of the parts of flanged heaters are made of stainless steel—an alloy that is mainly compri...
What is a Digital Controller?
Control panels are essential elements of any electrical device. Control panels are especially i...
Vegetable Oil Heating
Food Industries and Vegetable Oil Viscosity In Cleveland Ohio, a large food manufacturer called WATT...
A Closer Look At Load Banks
Load banks are essential for applications in a variety of industrial applications, especially for te...
Electric Heaters in the Nuclear Power Industry
The concept of Immersion Heater is quite simple. Just as the word suggests, it is a heating device t...
Temperature control in cold winter climates with flanged or circulation heaters.
With winter on the horizon, it is safe to say that everyone from man to machine is in need of adequa...
Electric Boiler Heaters For Clean Steam & Pure Steam
Steam is one of the best heat carriers in process industries. It’s used for everything from space ...
Mechanical Seals in Gas Heating
Keeping a heating system operating at peak performance requires all parts working properly. An impor...
Electric Heating Coils: Selection & Design
Electric heating coils transfer energy into heat in a variety of heating applications. They’re an ...
What is a Pressure Vessel?
Pressure vessels are carefully fabricated, enclosed containers designed for the purpose of holding e...
Duct Heating in HVAC and Building Construction
Heating, ventilation, and air-conditioning (HVAC) systems are used for heating and cooling residenti...
Temperature and Power Controls for Industrial Electric Heating
A control system is an essential part of every industrial heating system. Whereas some applications ...
.Crude oil, unprocessed fossil fuel, is one of the most important natural resources. In its unproces...